Taking control of emergency lighting
The digitisation of the modern workplace has paved the way for offices to become some of the most energy efficient buildings operating within the UK. Yet, in the event of a power cut during an emergency it is often ageing electrical infrastructure which is responsible for the safe evacuation of the building. With the UK’s commercial sector firmly focused on future-proofing its building stock, Steve Marr, an expert in power distribution at Legrand UK, warms of the risks linked to archaic emergency lighting practice.
Shedding a light on emergency systems
We are fortunate in the UK that we have excellent emergency services teams on hand to support us in times of crisis. However, despite fast response times, if disaster strikes in the workplace then employees must be able to quickly and safely exit the building, often well before the emergency services can arrive.
Given how disorientated you can find yourself in total darkness or smoke-filled corridors, an effective emergency lighting system is key to establishing familiarity and also highlighting the safest exit in the event of a fire or other emergency scenario.
Emergency lighting systems are a legal requirement in any public building, in line with BS5266-1:2011, and employers that fail to maintain their buildings to this standard will quickly find themselves facing hefty criminal charges. However, businesses and landlords risk complacency if they feel that such a system, which only just meets the minimum requirements, renders employees fully safe in the event of an emergency.
Given the ageing nature of much of the UK’s commercial building stock, many – as much as 80 per cent – of these emergency lighting systems are often examined and tested manually, generally during the middle of the night or when the building isn’t operational. Whilst such systems may have been installed in line with the requirements outlined by the British Standards, in the current age of advanced Building Management Systems (BMS), the maintenance practice has serious room for improvement given the potential risk for error it represents.
In the main, emergency lighting systems consist of self-contained emergency luminaires, whereby the emergency light is activated when the power is cut and an inverter transfers the power over to a built-in battery that takes over as the emergency power supply, powering the luminaire for a minimum of three hours.
Where potentially dangerous issues can arise is during the testing and maintenance process. In a typical emergency lighting installation, like many of those found across thousands of UK commercial buildings, a functional test of the emergency lighting system must be done once a month. This is where the power is cut and the emergency lighting is checked to ensure everything functions correctly. A full duration test must then also be undertaken once a year, which also involves cutting the power, but in this instance the battery output must also be checked after three hours of supply.
Whilst this system works in principle, relying on manual testing is not watertight given the technological advances that are now available in the market place. All it could take is one engineer to fail to spot a faulty fitting, forget to record a replacement that needs to be made, or write down the wrong fitting for a system to become a serious health and safety risk.
However, as is often the case, there is a simple solution. Many emergency lighting systems already operate using DALI protocol to control the luminaires, and in recent years we have seen the introduction of emergency lighting control systems which use both KNX and DALI, allowing for two-way communication between the luminaire and the control system. Making this upgrade to an advanced lighting control system, or considering it when commissioning either an extension or new build, can easily eradicate the risk of any emergency lighting system failure going unnoticed.
By using an advanced lighting control system, such as Electrak Buscom with Lightrak lighting control units, the end user and the luminaire can effectively communicate with each other. The end user is able to programme the luminaires to run the full three hour test at specific times, monitor all fittings, check they’re able to successfully switch into emergency mode and then report back on the status of the tests, what’s happened, whether there have been any failures and if any replacements need to be made. Crucially, it can also alert the building’s facilities manager if the lamps within the fittings are working or not. This is important as, even if the luminaire’s battery is working, if there is a fault with the lamp then the emergency system will fail.
However, an advanced lighting control system really comes into its own when feeding into a graphical interface connected to the BMS, sometimes known as a ‘head end’, which allows the end-user to extract all the information into an easily digestible format, as well as control scheduling of further tests. What’s more, end-users are also able to see a graphical representation of floor layouts with specific alert markers to point out where particular fittings aren’t working. It can even be programmed to deliver email or text alerts straight to the building maintenance team, informing them of any failures, and whether the problem is with the battery, the fitting, or the lamps, so they can fix them right away.
As such, there is no need for manual testing, and any potential faults can be recorded automatically, removing the risk of human error and any associated effects on an emergency lighting system.
Ultimately, from the end-user’s perspective, monitoring and controlling an emergency lighting system via the use of advanced lighting control will remove a very long-winded and time consuming maintenance process, as well as the associated risk of potential human error in not testing any lights correctly or failing to log any repairs that need to be made. In effect, it offers full reassurance that the emergency lighting system is fully operational and will be guaranteed to perform its essential job in the event of an emergency. Given the widespread advances in technology in recent years, employers cannot afford to fall short in this department. Investing in an advanced lighting control system can take the risk out of emergency lighting systems, giving employers peace of mind that – if disaster does strike – they can rely on their lighting system to guide employees to a swift and safe exit.